3000L/H Single Level Drinking Pure Water Purification Line
|FOB Price:||US $48,000 / Piece|
|Min. Order:||1 Piece|
|Min. Order||FOB Price|
|1 Piece||US $48,000/ Piece|
|Payment Terms:||L/C, T/T, Western Union, Money Gram|
- Model NO.: RO-3000
- Automatic Grade: Automatic
- Filling Valve Head: Multi-Head
- Dosing Device: Capacity Cup
- Packaging Container Lifting Structure: Chute Pneumatic Combination Lifting
- Packaging: Bottle
- Capacity: 3000L/H
- Material: SUS304
- Guarantee Time: 1 Year
- Transport Package: Blanket Cloth Package
- Origin: China
- Type: Volumetric Filling Machine
- Material Type: Liquid
- Feed Cylinder Structure: Single-Room Feeding
- Filling Principle: Pressure
- Structure: Rotary
- Packaging Material: Plastic
- Application: Pure Water Treatment Line
- RO Filter Level: Single Level Filter
- Trademark: YuFeng
- Specification: CE, ISO
- HS Code: 843880000
1. Application: used to filter the raw water to pure water for drinking or bottle filling or beverage making use.
Raw water: could be the river water, lake water, river water, dell water, city water etc, the filter level is made different as customer's real water quality.
Material: stainless steel 304 mateiral and food frade UPVC pipe and valve
2. Technology process:
Raw water tank---Water pump---Quartz sand filter---Active carbon filter---Precision filterW---Water buffer tank---Ro system---UV sterilizer---Pure water tank
3. Key machine in th line:
RO membrane is the key part of whole RO, it will decide the system workable or not. The water passing RO can remove bacterial, organic substance and microorganism.
No phase change will be generated in RO device during water purification. Water recovery rate is high, small in dimension, high automation.
Whole SUS304 rack, automation part apply AC contactor control, apply flow meter, pressure gauge and auto flush electrical magnetic valve, etc.
Protect device:Low pressure and high pressure protect switch is set before water entry and after water discharge. Booster pump and system will stop when water supply is not enough. Make cut off on booster pump when there is too much discharge pressure to avoid system running under pressure exceeding status.